What is the pressure loss of the climate ceiling?
The pressure loss at the connection points is determined in the engineering phase and follows from the so-called hydraulic calculations. In order to be able to make these, the ceiling drawings including installation components must first be made and the cooling and heating capacities to be supplied must be known to us. Based on this data, it is examined which panels should be activated and how the series / parallel circuits can be realized. When determining the series / parallel connections, we take into account a pressure loss on the connecting pipes of a maximum of 40 kPa unless other project-specific requirements have been set.